Click & drag mouse pointer left /right over image to rotate
Product reference key:
No suffix on product code = Zinc & Pass Plated
JS = JS500 Coating
BR = Brown Plastic Coated
SS = Stainless Steel
BS5440-1:2008 (section 9.2.1)
Where persons could come into contact with the terminal…. A protective guard shall be used. The guard shall be fitted such that no part of the guard is less than 50mm from any part of the terminal….. a suitable guard should be provided whenever a terminal if fitted less than 2.1m above ground, a balcony or a flat roof to which people have access. (For plume management kits)….. Where the inlet is less than 2.0m above ground level, a balcony or a flat roof a protective guard shall be used.
TERMINAL GUARDS FOR CONDENSING BOILERS
Zinc-plated terminal guards are unsuitable for use with condensing boilers. Plastic coated (polyethylene) guards are recommended for this application, and are available from Tower.
A SELECTION OF GUARDS ARE AVAILABLE BY REQUEST IN STAINLESS STEEL FOR A LIFETIME FIT. PLEASE CONTACT SALES FOR AVAILABILITY.